Underwriters Laboratories - UL &
ULC STANDARDS UPDATE (CAN/ULC-S524-14 - Includes Amendment 1) FOR WALL-MOUNTED HEAT DETECTORS!
Toronto, Ontario - January 24, 2017 - During the 7th meeting of the Working Group, the issue of wall mounting fire detectors was discussed and further clarified to address concerns regarding installation of heat detectors in this configuration. Sentence 126.96.36.199 of CAN/ULC-S524-14 (Amendment 1) is going to be amended as indicated in red below:
“Spot type fire detectors may be installed on a wall between 100 mm and 300 mm from the ceiling, measured to the top edge of the detector, only if prescribed for this application in the manufacturer’s published installation instructions. (Refer to Figure 6.)”
It’s important to note that this change won’t be incorporated into the Standard until the next version is officially published (sometime in 2018), but it does reflect how this Clause should be formally interpreted and applied. As of the date of this update there are NO heat detectors being sold in Canada that have been tested or are are listed for use in a wall-mounted configuration. Currently the ONLY exception to this rule applies to heat detectors installed in an elevator pit. Please reference the Fire Alarm System Device Installation Guide available from our TOOLS page for more information. You incur significant risk of having the installation rejected by the Verifier if you wall mount a heat detector.
ULC STANDARDS BULLETIN (CAN/ULC-S536-13)!
Toronto, Ontario - July 18, 2014 - Effective January 1st, 2015, ULC will be requiring all listed alarm companies to comply with the new changes in the referenced Standard (issued in October 2013) or risk losing their certification. Please review the 2014-03 Certification Bulletin (in English) or 2014-03 Bulletin de Certification (in French).
ULC STANDARDS BULLETIN (CAN/ULC-S537-13)!
Toronto, Ontario - July 18, 2014 - Effective January 1st, 2015, ULC will be requiring all listed alarm companies to comply with the new changes in the referenced Standard (issued in October 2013) or risk losing their certification. Please review the 2013-04 Certification Bulletin (in English) or 2014-04 Bulletin de Certification (in French).
UL FINDS MORE COUNTERFEIT SPRINKLER HEADS!
Northbrook, Illinois - December 31, 2014 - UL has issued another warning bulletin over counterfeit sprinkler heads being manufactured and sold in the (largely) South Asian market. So far, none of the heads they’ve identified have appeared in North America, but service technicians & sprinkler fitters must remain vigilant none-the-less!
UL ISSUES WARNING OVER COUNTERFEIT SMOKE DETECTOR!
Northbrook, Illinois - August 8, 2014 - UL has issued a special bulletin warning about a counterfeit Hochiki America Corp smoke detector. The model number is SLV-24N. This unit has NOT been properly tested by UL and bears a label with the word “foreign” misspelled on it. The text of the label reads: “Assembled in the U.S.A. of U.S. and Foreigh Parts”. Smoke detectors with this model number and label should be immediately removed from service and returned to the original seller. You can read more about this at http://www.newswire.ca/en/story/1396014/ul-warns-of-counterfeit-smoke-detector.
ULC STANDARDS BULLETIN (CAN/ULC-S561-13)!
Toronto, Ontario - July 25, 2013 - Effective September 30, 2013, ULC will be requiring all listed alarm companies to comply with the new changes in the referenced Standard (issued in April 2013) or risk losing their certification. Please review the 2013-11 Certification Bulletin.
DATA CABLE RECALL!
Rockville, Maryland - The U.S. Consumer Product Safety Commission (CPSC) has issued a bulletin regarding some data cabling sold primarily to homeowners through Home Depot. Even though the product is marked as being tested by UL, it does not meet the required fire rating. Home Depot is offering a full refund for the return of the product. Please visit the CPSC website for further information on what you should do.
MORE COUNTERFEIT SPRINKLER HEADS SURFACE!
Images are courtesy of UL/ULC®
COUNTERFEIT SPRINKLER HEADS!
Thermal Sensor Alert (March 2008):
Fire Extinguisher Agent Special Alert (June 2009):
CAN/ULC-S524-06 Amendment (February 2011):
Technical Support Contacts:
FIRE BLOCKADE (US):
FIRE BLOCKADE (Canada):
+1 (888) 340-3473
“We are not a professional union, but together, we are a union of professionals!”
What we’re all about!
We are not affiliated with ASTTBC, CFAA, CANASA, NFPA, NAFED, or NICET (although we encourage you to explore and objectively evaluate the benefits associated with supporting their individual efforts). Membership in the Fire Technicians Network is entirely voluntary. Are you up to the challenge of demonstrating your commitment to public safety and the highest standard of professional practice?
Copyright © 2007 - 2020 The Fire Technicians Network. All Rights Reserved