Fire Pump Controller RECALL: Affects pressure transmitters installed in Diesel fire pump controllers manufactured between September 1, 2007 and August 8, 2008 and in electric fire pump controllers manufactured between June 11, 2007 and August 8, 2008. Voltage transients may have adversely affected the GEMs 3100 series pressure transmitter which may cause it to read the incorrect pressure and fail to initiate the start sequence when required. For more information regarding product identification and installation instructions, please click here.
Contact Information: Corporate Headquarters Eaton Corporation Eaton Center 1111 Superior Avenue Cleveland, OH 44114-2584 Telephone: 216-523-5000
What we’re all about! We are not affiliated with ASTTBC, CFAA, CANASA, NFPA or NICET (although we will always promote their efforts). Membership in the Fire Protection Technicians Network is entirely voluntary. Are you up to the challenge of demonstrating your commitment to public safety and the highest standard of professional practice? JOIN US! And let us help take your career to the next level!