Discussion of verification issues and procedures.
- Posts: 11
- Joined: Tue Sep 03, 2013 4:36
Conducting verification on an added smoke detector. Tested new smoke detector and devices on either side and EOL for open, short, and ground.
My question is do I have to fill out CAN/ULC s537-04 appendix ''C'' or can I document the verification of the device on my work order.
- Site Admin
- Posts: 68
- Joined: Sat Aug 23, 2008 9:10
- Location: Vancouver, B. C., Canada
I'm assuming the added device was installed by an electrical contractor under a properly issued permit. I'm certain that the AHJ will be expecting something a little more than just a work order. You need to complete an Appendix "C" form. You need to document the functions that are affected by the installation at the control panel. You also need to perform your battery testing.