Blatantly advertising your services is strictly prohibited. Violators will be banned from posting. Identification with a company engaged in providing fire equipment service is encouraged in order to validate responses (i.e. a "tag line" which states your name, company's name and contact information is allowed).
- Posts: 3
- Joined: Thu Mar 07, 2013 7:29
directs that where the building is sprinklered, that a fault within one floor area shall not prevent voice communication in another. Is the fault referred to in the data loop serving active field device, and/or supporting field devices or does this refer to a fault in a voice communication circuit. In other words, does one have to split up voice communication speakers into different circuits when they serve different floor areas?
- Site Admin
- Posts: 70
- Joined: Sat Aug 23, 2008 9:10
- Location: Vancouver, B. C., Canada
If the floor area your are referring to is on a different fire alarm zone, then good engineering practice (and the intent of this Section which relates to distributed type systems) would entail a separate speaker zone as well or a buss isolator (added March 13, 2013).
I would recommend that you obtain the latest version of the Installation Standard which includes the February 2011 Amendment. The Amendment is, unfortunately, not available as a separate document (which, in my opinion, it should be).
+1 (888) 340-3473