Open forum for questions from the general public (property managers, resident managers, strata owners, etc.) relating to fire prevention & fire protection issues. Advertising of services is prohibited.
Blatantly advertising your services is strictly prohibited. Violators will be banned from posting. Identification with a company engaged in providing fire equipment service is encouraged in order to validate responses (i.e. a "tag line" which states your name, company's name and contact information is allowed).
- Posts: 7
- Joined: Mon Jul 26, 2010 7:53
Is AWM conductor suitable for a fire alarm install? Installed in conduit for the initiation circuit.
Some AWM is labelled AWM/TEW, which would be okay via Table 11.
- Site Admin
- Posts: 70
- Joined: Sat Aug 23, 2008 9:10
- Location: Vancouver, B. C., Canada
I don't believe it would be. Here's UL/ULC's "take" on it. "Unlike most wire categories, appliance wiring material (AWM) is a Recognized Component used in UL Listed or Classified end products. AWM wires are intended as factory-installed or factory-provided components of complete equipment submitted for investigation, rather than for direct separate installation in the field." (http://www.ul.com/global/eng/pages/offe ... eandcable/
Actually if they are TEW conductors and they are 16 gauge they are approved to be pulled in a raceway for FIre Alarm Systems. I would suggest tho to not take my code review as gospel and review the exact circumstance with your local electrical inspector. Although I can't imagine those conductors would be very cheap...